Hardware set up:
Dimmer 2 connected to:
Momentary switch x 2 (no light bulbs)
Home Centre 2
Parameter 28 has been set to 1
Scene ID is not being passed / triggered. I have created a basic debug LUA script and this is not triggering when I click the buttons (however the log at the top of the screen shows buttons are being pressed by reporting "ID 74 : Received parameter 13...".
Please login or register to see this code.
Trouble shooting done so far:
Dimmer 2 needs a load to start. If you don't want light bulbs on the output, the recommended way is to attach a "bypass 2" as load. You can add some bulbs to test, but if you trip the circuit breaker and it has no load, it won't start again. The FGS-223 is an alternative and does not require a load.