Search the Community
Showing results for tags 'contactor'.
Found 1 result
Want to use the double switch for two different cases for one lamp group: - continuous Q1 - flash mode Q2 I want Q1 and Q2 to be connected. S1 and S2 are not used. With Q2 disconnected, I can hear the switch 2 flashing. When they are connected, I get ONE single flash. Params: 15:5, 16:0, 18:20, 20: tested 0 and 2 Actually, my load is a relay contactor (for the real 6 kW load), but the real load is not yet connected... What is wrong?