Welcome to Smart Home Forum by FIBARO
as you can notice parts of Smart Home Forum by FIBARO is not available for you. You have to register in order to view all content and post in our community. Don't worry! Registration is a simple free process that requires minimal information for you to sign up. Become a part of of Smart Home Forum by FIBARO by creating an account.
As a member you can:
- Start new topics and reply to others
- Follow topics and users to get email updates
- Get your own profile page and make new friends
- Send personal messages
- ... and learn a lot about our system!
Smart Home Forum by FIBARO Team
I've got a comms box with terminal connects where all my lighting, power and switch wires feed into. I've attached the wiring diagram for this.
What I am confused with though is how to wire in the Bypass. I can connect 1 end of the Bypass into the switched live terminal with a jumper (Red A2's), however I dont know where the Bypass expects the other end of the feed to come from.
If I connect the other end of the Bypass into the global neutral as I have in my wiring diagram, is this going to cause issues, or does it need to be connected to the return wire from the lights before it gets to the global neutral terminals?
Please login or register to see this attachment.
Link to comment
Share on other sites
2 answers to this question
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.